Join Date: Jul 2011
Location: Western NY
Thanked 41 Times in 24 Posts
Ok, this might sound stupid, but where exactly is the evap inside the whole heater/AC box?
The more I think about it, the more I think you're correct about the fan blowing condensation off the evap. When the fan is on high I get a whole lot more water out the floor vents than when it's on a lower setting.
96 3500 Ext Cab dually, flatbed 4x4, NV4500, 4.10s, 262K, BHAF, 17*, 100 plate, AFC mods, 024 DVs, 3K GSK, benched by Farrell, Haley 5x.012s, Hamilton 178/208, 165 Beehives, O-ringed, 62/65/14, Coated pistons, ARP studs, South Bend 13" Con-OFE